모듈러시스템 / 해외 수출용으로 제작된 제품 입니다.
1.음성경보음 / 전면넥산 / 취급설명서 영문 또는 불어로 제작된 제품
2.전원사양은 110V/220V 50Hz 규격입니다.
3.소화가스수신기 / 모듈러 시스템에 적용
4.전자파시험 / 진동시험 / 충격시험에 적합한 제품
5.KFI기술기준과 축적된 경험으로 안전성을 최우선으로 고려하여 설계된 제품
6.제품 내부 부품은 SMD(표면실장기술) 부품으로 설계
*견적 및 기술 문의 : T.031-826-0410 / F.031-826-0430
* 기본 사양서*
Noduler System DSCP-1
1.BASIC CONFIGURATION AND GENERAL SPECIFICATION
What is receiving panel
Receiving panel plays a role of generating alarms by directly receiving signals generated
by detector or manual control panel or manual actuator.
Major functions of the product
1) Adopt high performance precision microprocessor in the product.
2) Implement a stable system by using processors and relays.
3) Install built-in auxiliary power supply (Ni-Cd Battery) which will automatically kick
immediately when power failure occurs.
4) When the system is actuated by detectors (A&B, A&C, or B&C),by pressure switch, or manually,
the contacts interlocked with the system will be activated(No voltage dry contact)
5) Manage main / auxiliary power supply by adopting a precision A/D converter in auxiliary
power monitoring circuit.
6) When the system is actuated by detector (A, B, or C), externally or manually, it is possible
to save the time of a fire, which can be confirmed via FND.
7) Check the status of built-in auxiliary power supply with an indicator lamp (Normal/Low)
which will turn on when the power level is less than 85% of the supplied voltage.
(Supplied voltage: DC24V, LED lamp starting voltage: DC20.4V)
8) Possible to maintain / repair by disassembling power supply part and terminal connection part.
※Options:When a detector circuit (A, B, or C) is activated, if another detector is not activated within 45 seconds, then the system will be automatically recovered
1) Model : DSCP-1
2) Type approval no : Su 10-22 / Type P Class 2 Complex Receiving Panel
3) Type : AC220V, DC24V, window-type, electronic relay, smoke control system (CO2, halides)
4) Rated voltage : AC110V/220V / 50Hz (Auxiliary power supply: Ni-Cd Battery DC24V/600mAh)
5) No. of circuit : 1
6) Material of cabinet : Steel 1.2t / Cream-colored powder coating (EK 427K)
7) Alarm : Main bell, sectional bell, buzzer, siren, voice alarm
8) Display : LED lamp (Light emitting diode)
9) Discharge timer : Use FND (digit display)
10) External connection device : main bell, sectional bell, detector, manual control panel,
discharge lamp, siren, solenoid valve, pressure switch
11) Interlocking of auxiliary receiving panel : If an output is occurred by a detector (A, B, or C),
or manual actuation, or gas release, then the system can be used by interlocking with no
voltage dry contact
12) Operating temperature : -10 C ~ 50 C
13) Relative humidity : RH 10% ~ 90% (With no condensation)
14) Cabinet dimension : 250mm x 360mm x 85mm